Education and Science»
Insulating supplies used in transformers
Up to date on August 28, 2014 OSBERT JOEL C moreContact Creator Learn more on transformers
How does a transformer work?
Elements of a Energy Transformer
Equal circuit and Phasor diagram of transformers
Losses in Transformers
Testing of transformers
Cooling of Transformer
Tap Changing in transformers
What is a Buchholz relay? How does it work?
Properties of transformer oil
Insulating supplies utilized in transformers
Present transformer- Definition, Principle, Equivalent circuit, Errors and kinds
Potential Transformers in detail
How does an Autotransformer work?
Insulation is one among an important constituent of a transformer. The durability and stability of the transformer depends upon the right utilization of insulating materials in it. In transformers mainly three insulating supplies are used.
Of the three, the most important insulating material used is transformer oil.
As stated earlier transformer oil is the most important insulating material utilized in transformer. It is among the essential factors that decide the life and passable operation of the transformer.
The transformer performs the following two capabilities.
1. It supplies insulation together with the insulating materials used within the conductors and coils.
2. It additionally acts as a coolant to extract heat from the core and the windings.
Transformer makes use of hydrocarbon mineral oil. It mainly consists of 4 generic classes of organic compounds. They’re aromatics, paraffins, napthenes and olefines. Transformer oil will present higher insulation when aromatics, paraffins, napthenes and olefines are present in it at a proper proportion. Transformer oil is desired to have more of saturated paraffins and fewer of aromatics, napthenes and olefines for higher insulation. For extra stability, more aromatics and napthenes are necessary. To get transformer oil at insulating property and stability, there have to be an optimum mix of four natural elements. This can be obtained by careful refining of crude oil. Vegetable and animal oils cannot be utilized in transformers as a result of they type fatty acids and assault the fibrous insulating supplies.
The transformer is affected by its operating situations. The presence of moisture or suspended particles in transformer oil affects its dielectric property. Hence transformer oil it must be tested periodically. If the oil is containing moisture or suspended particles it ought to be filtered or replaced by recent oil.
Bodily constants of Transformer oil
Thermal conductivity 0.12 W/m deg C
Particular Heat 2.06 kJ/kg deg C
Co-efficient of Growth 0.00078/ deg C
Imply density issue zero.00065/ deg C
The above parameters are primarily based on IS 335 Insulating paper
Insulating paper is made from the vegetable fibers. These fibers primarily consist of cellulose. The primary properties of these papers are listed below:
Grammage is the ratio of mass to the area. It influences many of the electrical and mechanical properties. The advisable worth for 125 micrometer thick paper is 100 gm/mt2.The maximum allowable variation is 5%.
The paper really helpful in transformer use can have a density vary of 0.6 to 1.3 gm/c.c.
Moisture content material
Moisture content reduces the dielectric property of the paper. Since paper is hygroscopic, moisture ingression takes place with utilization. The maximum allowable moisture content material is 8%.
Oil and water absorption
The dielectric property of paper increased when impregnated in oil underneath vacuum and decreases with water content material. Regardless that the water content material is just not advisable the maximum permitted water content material is 10%.
Permeability is the rate at which the air can cross by way of it. The dielectric power of paper is inversely proportional to the air permeability. The beneficial worth of air permeability is 0.2-zero.5.
Tensile strength and elongation
Paper should be capable of withstand the tension throughout wrapping. Recommended worth of tension is 78 – 85 N-mt/gm in wrapping direction and 25 – 30 N-mt/gm.
The electrical parameters of insulating paper are indicated under.
Property Recommended Value
Break down voltage 7- 7.5 kV/mm (min) at ninety deg. C
Dissipation issue zero.003 (max)
Conductivity 10 ns/mt (max)
Press board is also made up of vegetable fibers and accommodates cellulose. Stable press board unto 6 mm to 8mm thick is ordinarily made. Since probably the most difficult insulation drawback in HT transformer occur at the ends of the windings and lead outs from the windings hence moulded pressboards are broadly utilized in these elements for insulation. Synthetic resin bonded paper based mostly laminates are utilized in voltage burdened zones. The necessary parameters considered are density, tensile strength, elongation, conductivity, oil absorption, moisture content, compressibility and many others.
A complete Electrical Engineering reference information
Electrical Engineering: Rules and Functions (fifth Version) Buy Now Associated
Education and ScienceInsulating materials used in fashionable Electrical Machines
by OSBERT JOEL C0
Supplies top:75px” class=”thumbphoto”>Electrical EngineeringPotential Transformers intimately
by OSBERT JOEL C5
Supplies height:75px” class=”thumbphoto”>Normal ChemistryAll About Matter
by Liwayway Memije-Cruz179
ChemistryFacts About Quartz—Properties, Types, top:75px” class=”thumbphoto”>ChemistryTypes of Chemical Reactions
sendingamar dubey eight months in the past
What are the type of insulators used in transformer windings
ravi Trivedi 2 years in the past
How to identify shell form transformers ? what are the parameters.
I have noticed core steel used in shell form transformers when dis assembled and examined , out of used unit, it provides very irritating result in core loss, why? what makes it poor in high quality.
Rajinder kumar 2 years ago
Power transformer is shell tye transformer
AuthorOSBERT JOEL C three years in the past from CHENNAI
Thanks Mr.KUNJESH KAMBODI
KUNJESH KAMBODI three years in the past